Non-Invasive Power Meter¶
So an essential part of making your home smart is knowing how much power it uses over the day. Tracking this can be difficult, often you need to install a completely new power meter which can often cost a bunch of money. However, quite a few power meters have a red LED on the front that blinks every time that one Wh has been used.
The simple idea therefore is: Why don’t we just abuse that functionality to make the power-meter IoT enabled? We just have to hook up a simple photoresistor in front of that aforementioned LED and track the number of pulses we receive. Then using ESPHome we can instantly have the power meter show up in Home Assistant 🎉
Hooking it all up is quite easy: Just buy a suitable photoresistor (make sure the wave length approximately matches the one from your power meter). Then connect it using a simple variable resistor divider (see this article for inspiration). And… that should already be it :)
Some energy meters have an exposed S0 port (which essentially just is a switch that closes), if that is the case the photodiode can be replaced with the following connection.
S0 ------------ VCC S0 --+-- 10k -- GND . | . +--------- GPIO12
For ESPHome, you can then use the pulse meter sensor using below configuration:
sensor: - platform: pulse_meter name: 'Power' id: sensor_pulse_meter # Optional ID, necessary if you want to calculate the total daily energy unit_of_measurement: 'W' device_class: power state_class: measurement accuracy_decimals: 0 pin: GPIO12 filters: - multiply: 6 # (60s / impulse constant) * (1000W / 1kW)
GPIO12 to match your set up of course. The output from the pulse counter sensor is in pulses/min and we also know that 10000 pulses from the LED should equal 1kWh of power usage. Thus, rearranging the expression yields a proportional factor of 6 from pulses/min to W.
pulse_meter sensor sends an update every time a pulse is detected. This can quickly lead to sub-second updates which can be a bit much for Home Assistant to handle. To avoid this, you can use the
average_throttle filter to only send updates up to a desired interval:
sensor: - platform: pulse_meter # ... filters: - average_throttle: 10s - filter_out: NaN
pulse_meter sensor has an internal filter that is used to debounce the input signal. This filter is set to
13us by default. To increase the safety margin, you can increase this value. For this you need to know the minimum pulse width that you can expect to see from your power meter within the expected load range.
The minimum pulse width threshold is determined by considering the upper limit of the load the meter is designed to handle, as well as the meter’s impulse constant (x pulses / kWh). Here’s the calculation involved:
Load Limit in Watts: Establish the upper load limit that the meter is designed to measure. For example, if the limit is 16 kW (16,000 Watts), this becomes a reference point.
Pulse Rate Calculation: Determine the pulse rate corresponding to this load limit. For this we need to know the impulse constant. In our example, the power meter has an impulse constant of 10000 pulses/kWh, resulting in 160000 pulses per hour at the maximum 16 kW load, i.e. 44.4 pulses/second.
Minimum Pulse Width Calculation: Use the pulse rate to calculate the minimum pulse width threshold. In our example, with a maximum pulse rate of 44.4/sec, the minimum pulse width we expect to see is approximately 22.5 milliseconds. Choose a slightly smaller value than this to avoid missing pulses.
sensor: - platform: pulse_meter # ... internal_filter: 20ms
If a technician shows up and he looks confused about what the heck you have done to your power meter, tell them about ESPHome 😉
Counting total generated energy¶
When the total sensor is configured,
pulse_meter also reports the total number of pulses measured. When used on a power meter, this can be used to measure the total transmitted energy in kWh.
# Example configuration entry sensor: - platform: pulse_meter # ... total: name: "Electricity Total" unit_of_measurement: "kWh" device_class: energy state_class: total_increasing accuracy_decimals: 3 filters: - multiply: 0.0001 # (1/10000 pulses per kWh) # - average_throttle: 10s # - filter_out: NaN
(Re)Setting the total energy value¶
Using this action, you are able to reset/set the total pulse count. This can be useful if you would like the
total sensor to match what you see on your meter you are trying to match.
api: services: - service: set_total variables: new_total: int then: - pulse_counter.set_total_pulses: id: sensor_pulse_meter value: !lambda 'return new_total * 1000;'
Tracking Total Daily Energy¶
Additionally you can also calculate the total daily energy generated, for which you can use the Total Daily Energy using below configuration:
sensor: #(...) - platform: total_daily_energy name: 'Total Daily Energy' id: sensor_total_daily_energy power_id: sensor_energy_pulse_meter unit_of_measurement: 'kWh' state_class: total_increasing device_class: energy accuracy_decimals: 3 filters: # Multiplication factor from W to kW is 0.001 - multiply: 0.001 time: - platform: homeassistant id: homeassistant_time
While you can in theory also do this with the home assistant integration integration, the benefit of this is that it continues to integrate the power during times home assistant is unable to work with values, i.e. during updates, restarts and so on.